The following procedure will be initiated when an alarm condition occurs:
If a Trouble condition occurs with any of the field wiring or internally supervised circuits, a Trouble condition is displayed on one of the front panel LEDs.
ll Alarm and Trouble conditions are annunciated via an LED flash code sequence. The flash code displayed by the Service System LED and corresponds to the indicated zone and condition I.D. The flash code list is printed on the front panel label of the AdvantageLi electronics module. The flash code guide can also be found on in the previous page.
Two actuation circuits are each capable of actuating up to six Stat-X© aerosol generators or similar devices on two separate zones. Power to fire the actuators is delivered from a bank of super capacitors.
The front panel located Push to Test button can be pressed which will flash all of the LEDs ON, sound the audible buzzer but will not transfer I/O relays.
To perform a Field Wiring Sensor Test:
The Advantage Lithium Panel Is equipped with a battery disconnect toggle that electronically disconnects both the primary and secondary batteries. This function disables the AdvantageLi panel and may be used when transporting, shipping, or storing the AdvantageLi control panel for extended periods.